CAN/ULC-S PERIODIC INSPECTIONS AND TEST – DAILY AND MONTHLY. NOTE: Refer to Appendix D for examples of Inspection and Test Record. SCOPE. This Standard provides requirements for the inspection and testing of fire alarm systems and specifies the devices and functions to be inspected. 1 SCOPE This Standard prescribes requirements for the inspection and testing of fire alarm systems and specifies the devices and functions.
|Country:||Antigua & Barbuda|
|Published (Last):||21 July 2017|
|PDF File Size:||14.14 Mb|
|ePub File Size:||10.79 Mb|
|Price:||Free* [*Free Regsitration Required]|
Reducer and cap are not missing? It’s a good idea to check the battery compartment every six months for leakage or corrosion on the terminals. Building Life Safety Audits. Description of the function of each operating control and indicator on the fire alarm control unit. Yes No Last Service Date: J Upon failure of one amplifier, system automatically transfers to backup K amplifier s. cwn
Fire Alarm System Periodic Inspection (CAN/ULC-S)
Where fault isolation in power distribution riser has been provided, tests have been conducted to ensure a wire-to-wire short in the field s36 between each pair of control units or transponders, in C turn, results in annunciation of the fault and continued operation outside of the shorted section confirmed.
No leaks are present? Fifth year inspection items. Where hearing impaired patients or w536 are located, it is usual to have strobe lights located along corridors and in individual rooms to indicate an emergency condition exists in the building. Where active and supporting field devices are utilized, device labels correspond with actual field location.
Latches functional including break-glass type? Check-valves internally inspected and all parts operate properly, move freely, and are in good condition? L Inspected for electrolyte leakage. Minimum of one alarm zone ulf one supervisory zone tested per annunciator or sequential display to confirm operation.
For homeowners with ten year old multi-station type smoke alarms or who may be contemplating changing or upgrading hlc existing units! Yes No Pump run for ten 10 minutes Test log reviewed via visual display at controller?
Standards Council of Canada
Required Building Code Alarm Operation: Swing out Racks – lubricate and ensure proper operation. C F Discharge pressure at gauge: Test exhaust for excessive back pressure? Visible signaling appliances tested? Indicate type of test performed on a fully charged battery select one: All sprinkler pressure regulating control valves passed full flow test? Buildings – prior to freezing weather?
Control valves shall be inspected. Operation of the fire signal receiving centre transmitter bypass means results in a specific I trouble indication at the fire alarm control unit or transponder Operation of the fire signal receiving centre disconnect means transmits a trouble signal to J the fire signal receiving centre.
CAN/ULC-S Fire Alarm Annual Inspection Test Form
Alarm valves shall be inspected externally. Your service agency MUST identify those detectors that it could not perform this test on.
Magnetic door holder ca activated by fire alarm system? Batteries 2 voltage readings are normal Check accuracy of pressure gauges and sensors? Switches for ancillary functions operate as per design and specification.
Manual transfer from alert signal to alarm signal. The montly test is to ensure that all audible and visual alarm indicators function properly and are loud or visible enough to alert all the occupants to a fire condition. Cabinets easy to fully open? Is the building occupied?
CAN/ULC-S536-04 Fire Alarm Annual Inspection Test Form
Please attach testing data sheets for each system tested. Jockey pump operational and in good condition? Ulx sprinklers less than 50 yrs old. There is a possibility that you may inadvertently set off the fire alarm system.
Tamper switches inspected covers secured, leaks or corrosion? Description of alarm signal operation.