Publication UMA-EN-P – November Table of Contents . User Manual UM to assign an IP address to the MicroLogix. controller. Publication INC-EN-P – October Important . Manual UM .. publication UM, for more information on surge suppression. rm_-en-p – Free ebook download as PDF File .pdf), Text File .txt) or read book online for free. Document Number IN UM
|Published (Last):||28 May 2016|
|PDF File Size:||1.94 Mb|
|ePub File Size:||8.99 Mb|
|Price:||Free* [*Free Regsitration Required]|
Identifies information about practices or circumstances that can lead to personal injury or death, property damage, un001 economic loss. Each product is supplied with markings on the rating nameplate indicating the hazardous location temperature code. Specifically, this equipment is intended for use in clean, dry environments Pollution degree 2 1 and with circuits not exceeding Over Voltage Category II 2 IEC 3.
1766-IN001 – Rockwell Automation
Without appropriate precautions, there may be potential difficulties ensuring electromagnetic 1676 in other environments due to conducted as pp as radiated disturbance. Switching inductive loads without surge suppression can significantly reduce the life of relay contacts or damage transistor outputs. Because of this difference, and also because of the wide variety of uses for solid state equipment, all persons responsible for applying this equipment must satisfy themselves that each intended application of this equipment is acceptable.
Secure any external connections that mate 166 this equipment by using screws, sliding latches, threaded connectors, or other means provided with this product.
Replace the battery when the controller is powered on.
Be sure that power is removed or the area is nonhazardous before proceeding. For AC-powered controllers, this connection must be made for safety purposes. Trademarks not belonging to Rockwell Automation are property of their respective companies. Follow these guidelines when you handle this equipment: This could cause an explosion in hazardous location installations.
Combinations of equipment in your system are subject to investigation by the local Authority Having Jurisdiction at the time of installation. By using suppression, you also reduce the effects of voltage transients caused by interrupting the current to that inductive device, and prevent electrical noise from radiating into system wiring.
No patent liability is assumed by Rockwell Automation, Inc. It must be mounted within an enclosure that is suitably designed for those specific environmental conditions that will be present and appropriately designed to prevent personal injury resulting from accessibility to live parts. Output group to output group isolation Verified by one of the following dielectric tests: Once wiring is complete, be sure the controller is free of all metal fragments before removing the protective debris strip.
This equipment is supplied as open-type equipment. When you connect or disconnect the battery an electrical arc can occur. Debris strip ATTENTION Do not remove the protective debris strip until after the controller and all other equipment in the panel near the controller are mounted and wiring is complete. When the battery is low, the indicator is set displayed as a solid rectangle. The Belden cable has two signal wires black and clearone drain wire, and a foil shield.
Follow these steps to install your un001 using mounting screws. At this level transient voltages are controlled and do not exceed the impulse voltage capability of the product’s insulation. Wire fragments that fall into the controller could cause damage.
Plug the ribbon cable connector into the bus connector. For an additional level of technical phone support for installation, configuration and troubleshooting, we offer TechConnect support programs.
Throughout this manual, when necessary, we use notes to make you aware of safety considerations. Secure the battery connector wires so that it does not block the expansion bus connector as shown below. The enclosure must have suitable flame-retardant properties to prevent or minimize the spread of flame, complying with a flame spread rating of 5VA, V2, V1, V0 or equivalent if uj001. If you would like a manual, you can: Repeat steps 1 and 2 for the second DIN rail latch.
For more information on proper grounding guidelines, see the Industrial Automation Wiring and Grounding Guidelines, publication